Service and Maintenance
A visual inspection every six months and a yearly wet pressure test is required as per BS9990/2015. Failure to do so may invalidate your insurance.
Annual Pressure test.
For dry risers they must be tested with water to 12 bar and hold the pressure for 15 minutes.
Check all valves are closed and padlocked, outlet washers are in good condition, and inlet breeching and cabinet is in good condition. All required signage is present and correct.